50+' 12/4 with ground MC Cable New For Sale
This item has been shown 82 times.
50+' 12/4 with ground MC Cable New :
This Listing is for 50'
12/4 With ground MC Cable
Conductorsare Black Red BlueWhiteGreen(5)
This is new old stock unused MC cable
always a little longer than
Always Fast Shipping!
Thanks for looking Have a
Some product info below
This 12/4 with ground MC
Cable is constructed with soft-drawn copper, With 4#12 type THHN/THWN conductors rated 90°C + 1 #12 green
insulated grounding conductor. The conductors are cabled together. Aluminum interlocking armor is applied over the assembly.
12-4C Metal Clad (MC) Cable PlusGround, Aluminum Armored, Solid Copper Conductors
Metal Clad Cable may be used for branch, feeder and service for distribution in commercial, industrial, and multi-residential construction. They are suitable for installation in motion picture studios, theaters, and places of assembly (100 people or more) per NEC Articles 230.43, 300.22(C), 330, 396, 518, 520, 530 and 645. These cables may be installed in approved raceways and as open runs of cable on a messenger. They may be installed exposed, concealed or in cable tray and may be run in spaces used for environmental air in accordance with NEC Article 300.22(C) ONLY.
Solid conductors and the wires for stranded conductors are soft annealed copper to ASTM B3. PVC/Nylon type THHN insulation in accordance to UL 83, flame resistant, meeting UL VW-1. Bare copper ground wire, sized in accordance with NEC and UL, with green THHN insulation. Conductors are cabled with grounding wires. A marker tape/core protection tape combination assembles the core in an essentially round configuration. Interlocking galvanized steel tape armor applied directly over the core. flame test.
- Meets UL 83: Thermoplastic Insulated Wires and Cables
- Tested to UL 1479: Fire Tests of Through-Penetration Firestops for one, two or three hour fire rated assemblies (for cables up to #2 AWG)
- Meets UL 1569: Metal Clad Cables
- Meets UL 1581: Reference Standard for Electrical Wires, Cables, and Flexible Cords
- Meets UL 2256: Wire and Cable Test Methods
- Designated Type MC per NEC Article 330
Conductors:4 + (1) Ground
Outside Diameter:0.544 inches
Ampere Rating THHN:20
500’ Belden 9514-500-60 Cable - Nos
800 Ft Belden 9451 22 Awg 1-pair Shielded Audio Cable
75' 4/3 Copper Nm-b Romex With Ground Nonmetallic Sheathed Cable 600v Black
Southwire 10/2 W/ground Romex 100' Nm-b Indoor Wire New